Versatile SE 400 and SE 800 Electrostatic
Air Cleaners are made to
install recessed into a drop ceiling or against a hard surface such
as a permanent ceiling or wall.
Recessed Flush Mount in
For a flush appearance, install
electrostatic air purifiers partially recessed into the drop ceiling.
They will be securely
fastened to the permanent ceiling above. You may need a second
person to support the air cleaner while installing.
Not support weight of air cleaner from suspended drop ceiling rails.
To make it easy, remove the collection cells and filters before
Unpack the unit from the box. Unlatch the filter access door
and remove the collection cells and pre-filters.
Step 2: Use large diameter
washers and lock-nuts to install ¼-20 eyebolts. Threaded drop
rods can be used instead of eyebolts. Install trim onto the air
cleaner at the level where the drop ceiling will reach the air
cleaner. See sketch A below.
Step 3: Remove the ceiling panels
around the area where the electrostatic air cleaners will be placed. Decide
where and how the safety chains or threaded rods will secure to the
ceiling joists, permanent ceiling, etc.
Step 4: Measure out the chains
and attach them to the 4 eye bolts on the electrostatic air
purifiers ( or fasten
threaded rods ).
Step 5: Lift air cleaner into
position and support it while fastening chains or rods to ceiling
joists, permanent ceiling, etc. See sketch A below.
Step 6: Make electrical
connections as described below in
Step 7: Re-install collection
cells and pre-filters. Close access doors and your
electrostatic air cleaners are
ready for operation.
Return to Top
Surface Mount on Solid Ceiling